Even if the company does not have enough land area to build a sewage treatment facility, industrial wastewater treatment equipment can be buried and installed in parking spaces and green belts. After the industrial waste water treatment equipment is buried, the equipment is covered with soil, which can be treated with greening and surface hardening, and can be reused as a parking lot to solve the problem of land occupation.
Industrial wastewater treatment equipment is a molding equipment that can be processed according to the actual site conditions of the enterprise, and can be placed directly on hardened ground without civil construction. Bring huge advantages in space.
The entire system of industrial wastewater treatment equipment consists of nine parts, which are controlled by PCL, and then can be automatically treated, and the normal treatment of water can be reduced to the peak and trough stages. Features of industrial wastewater treatment equipment: The entire set of equipment can be buried underground without occupying land; the top can be beautified. High degree of purification, less sludge in the entire system; high degree of automation, low energy consumption, easy handling, and fewer personnel. The noise produced is low, the smell is small, and the impact on the surrounding environment is small.
Dosing operation of industrial wastewater treatment equipment: First open the water inlet valve in the mixing tank, put a certain amount of industrial water to dissolve the drug, start the mixer, put a certain amount of the drug into the mixing tank, and require the coagulant to be stirred For 5 to 10 minutes, the coagulant should be stirred for about 30 minutes: After mixing is complete, open the outlet valve of the mixing tank and the outlet valve of the metering pump. When the sewage lift pump is running, the metering pump can be started for medicine. When one drug is finished, it can be dispensed into another mixing tank for use.
The metering pump is connected to the sewage pump, and the metering pump automatically adjusts the metering amount according to the flow signal input by the electromagnetic flowmeter through the frequency converter. When draining water into the mixing tank and adding drugs to the mixing tank, the outlet valve of the other mixing tank should be closed. When you need to maintain industrial wastewater treatment equipment, turn it off. For related valves, open the corresponding vent valve when servicing the mixing tank.